DWSD - Water Works Park Water Treatment Plant - Executive Summary
Clean Air Act Amendments Section 112(r)(7) |
Accidental Release Prevention Programs:
40 CFR Part 68 - Subpart G
Risk Management Plan
The Detroit Water and Sewerage Department's Water Works Park Water Treatment Plant is a stationary source that is subject to the Risk Management Programs under the Clean Air Act, Section 112 (r)(7) (as promulgated in 40 Code of Federal Regulations Part 68). The Water Works Park Water Treatment Plant stores chlorine in quantities in excess of the 2,500 pound Risk Management Program threshold.
Pursuant to 40 CFR ' 68.150, the Water Works Park Water Treatment Plant is required to submit a single Risk Management Plan (RMP) that includes the information required by '' 68.155 through 68.185. The Water Works Park Water Treatment Plant is also required to provide an executive summary in the RMP. The following is a brief description of various elements of the facility's Risk Management Program, as required by 40 CFR ' 68.155:
(a) THE ACCIDEN
TAL RELEASE PREVENTION AND EMERGENCY RESPONSE POLICIES AT THE STATIONARY SOURCE
The Detroit Water and Sewerage Department (DWSD) operates five water treatment plants in the Southeast Michigan area. While the production of potable drinking water is vital to the welfare of the community, DWSD recognizes that the safe handling of the chlorine used in the water disinfection process is also critical to the welfare of the community. DWSD recognizes that the U.S. Environmental Protection Agency lists chlorine as a regulated toxic substance pursuant to the Accidental Release Prevention and Risk Management Program regulations.
DWSD is committed to the implementation of stringent safety precautions for chlorine handling at all of its water treatment facilities. These safety precautions are necessary to prevent accidental releases of chlorine that could threaten the health of DWSD employees, DWSD contractors, and the members of the community DWSD serves. To this end, DWSD implements routin
e equipment maintenance and process improvements, operational procedures, employee training programs, and emergency response procedures, and is committed to compliance with all applicable state and federal regulations.
(b) THE STATIONARY SOURCE AND REGULATED SUBSTANCES HANDLED
The Water Works Park Water Treatment Plant treats water from the Detroit River to produce potable drinking water. Water from the Detroit River flows via gravity through an underground tunnel to the Water Works Park Water Treatment Plant. The plant typically produces 120 million gallons per day (MGD) of treated water.
The plant adds aluminum sulfate (alum) to the water to aid in the removal of particulate matter. The alum produces a precipitate that binds to fine particles; the resulting larger particles settle out. On an as-needed basis, the plant uses its carbon system to add activated carbon to the water. Activated carbon can remove tastes and odors that may exist in the influent water. The plant us
es its fluoride system to add fluoride to the water. The fluoride provides water consumers with protection against tooth decay. The plant also adds phosphoric acid to the water to minimize the leaching of lead from water distribution piping. The plant's alum, carbon, fluoride, and phosphoric acid systems do not contain chemicals that are designated as regulated toxic or flammable substances pursuant to the Accidental Release Prevention and Risk Management Program regulations.
The plant's chlorine system disinfects the water. The water disinfection occurs at the beginning of the treatment process (in the Pre-Chlorination Building) and as a final treatment step (in the Post-Chlorination Room). The primary components of the plant's chlorine system for both pre-chlorination and post-chlorination include a maximum of ninety (90) 2,000 pound cylinders of chlorine, nineteen (19) evaporators, eleven (11) chlorinators, and the associated chlorinated water distribution components (e.g.,
polyvinylchloride piping). The facility's Pre-Chlorination Building is equipped with a chlorine abatement system (water scrubber) that is capable of removing the contents of one 2,000 pound cylinder of chlorine.
Chlorine is designated as a "regulated toxic substance" pursuant to the Accidental Release Prevention and Risk Management Program regulations. The Water Works Park Water Treatment Plant has more than the threshold quantity (2,500 pounds) of chlorine in its water disinfection process; therefore, the attached Risk Management Plan addresses this single covered process.
(c) THE WORST-CASE RELEASE SCENARIO AND THE ALTERNATIVE RELEASE SCENARIO, INCLUDING ADMINISTRATIVE CONTROLS AND MITIGATION MEASURES TO LIMIT THE DISTANCES FOR EACH REPORTED SCENARIO
The U.S. Environmental Protection Agency's Risk Management Program guidance document for Wastewater Treatment Plants (Chapter 4: Offsite Consequence Analysis) was referenced in the development of the worst-case and alternative re
lease scenarios for the Water Works Park Water Treatment Plant.
The Worst-Case Release Scenario involves the release of the entire contents of the greatest amount held in a single vessel (i.e., 2,000 pounds of chlorine gas) within an enclosure (building). Assuming a wind speed 1.5 meters/second, atmospheric stability class F, relative humidity 50%, a maximum air temperature of 770F, a release duration of 10 minutes, and a ground level release in an urban area, the toxic endpoint for chlorine (0.0087 mg/L or 3 parts per million) would be located within 0.98 miles of the Water Works Park Water Treatment Plant.
The Alternative Release Scenario assumes that the outlet valve on one 2,000 pound chlorine cylinder leaks from a 1/8 inch diameter opening, and that the release occurs within an enclosure (building). Assuming a wind speed of 1.5 meters/second, atmospheric stability class D, relative humidity 50%, a maximum air temperature of 770F, a release duration of 13 minutes, and a ground
level release in an urban area, the toxic endpoint for chlorine (0.0087 mg/L or 3 parts per million) would be located within 0.17 miles of the Water Works Park Water Treatment Plant.
It should be noted that the Pre-Chlorination Building at the Water Works Park Water Treatment Plant is equipped with a water scrubber that is capable of removing the contents of one 2,000 pound cylinder of chlorine. A release from the Pre-Chlorination Building would not result in any off-site release if the scrubber was functioning properly.
(d) THE GENERAL ACCIDENTAL RELEASE PREVENTION PROGRAM AND CHEMICAL-SPECIFIC PREVENTION STEPS
The Water Works Park Water Treatment Plant stores, handles, and uses chlorine in its water purification process. The Water Works Park Water Treatment Plant has established a Process Safety Management Plan. The information contained within this PSM Plan establishes the protocols and procedures needed to safely handle and use chlorine. The plan is designed to prevent and mi
nimize the effects of an unplanned, sudden or non-sudden incident involving chlorine. This plan is designed to meet the regulatory requirements of MIOSHA, Rule #40819102 - Process Safety Management Program.
Specifically this plan protects the community using a combination of operating procedures and safe work practices, equipment design, emergency operations and shut-down procedures, building design, containment, chlorine scrubbing equipment, and employee training and education.
The requirements of the Process Safety Management Plan will be implemented as an on-going compliance policy to ensure that chlorine is safely stored, handled, and used by the Water Works Park Water Treatment Plant. This plan provides direction for the current and future use and handling of chlorine, and ensures that any release of chlorine can be safely contained and neutralized so as to minimize its impact on the community.
(e) THE FIVE-YEAR ACCIDENT HISTORY
In the last five years at the Water Works Park
Water Treatment Plant, there have been no reportable releases of chlorine or chlorine releases that have resulted in deaths, injuries, or significant property damage on site, or known offsite deaths, injuries, evacuations, sheltering in place, property damage, or environmental damage.
(f) THE EMERGENCY RESPONSE PROGRAM
The Water Works Park Water Treatment Plant has a documented Chlorine Emergency Response Plan. The Water Works Park Water Treatment Plant is also included in an Emergency Response Plan that was developed for all Detroit Water and Sewerage Department (DWSD) facilities. The DWSD Emergency Response Plan has an appendix that specifically addresses accidental releases of chlorine. The plans address the notification of local emergency response agencies and the public, emergency first aid and medical treatment, response strategies and incident command, evacuation procedures, and specific procedures for responding to chlorine releases.
Water Works Park Water Treatment Plan
t personnel that have the potential for responding to accidental releases of chlorine have received formal emergency response training (i.e., 40-Hour Hazardous Waste Operations and Emergency Response (HAZWOPER) training). In addition, the plant's chlorine supplier has routinely provided chlorine-specific emergency response training to plant employees.
The Water Works Park Water Treatment Plant's Pre-Chlorination Building is equipped with two (2) chlorine detectors. The Post-Chlorination Room is equipped with one (1) chlorine detector. If a chlorine detector in the Pre-Chlorination Building senses chlorine at a concentration of 1 part per million or greater, a red flashing light will be activated outside the building and an audible alarm will sound in the laboratory and in the Senior Operator's booth in the High Lift Building. If the detector in the Post-Chlorination Room senses chlorine at a concentration of 1 part per million or greater, a red light will be activated and an au
dible alarm will sound throughout the building. Three operators are on site at all times to respond to an alarm. The external notification of local emergency response agencies and the public would be conducted on an as-needed basis, in accordance with the facility's Emergency Response Plan.
In the event of a release, the Water Works Park Water Treatment Plant's Pre-Chlorination Building is equipped with a water scrubber that is capable of removing the contents of one 2,000 pound cylinder of chlorine.
(g) PLANNED CHANGES TO IMPROVE SAFETY
The Water Works Park Water Treatment Plant is in the process of constructing a new plant that is scheduled for completion in December 2002. Construction of the new Water Works Park Water Treatment Plant began in the spring of 1999. The plant will include a new chlorine system for pre-chlorination and post-chlorination. In addition, the new plant will utilize an ozonation system for water disinfection.
The Water Works Park Water Treatment Pl
ant is in the process of updating and revising its current Emergency Response Plan.
The City of Detroit is also initiating the use of a new computer program for purchasing, training, and preventive maintenance. This computer program will be used by all City of Detroit operations, including the water treatment plants. When the program is fully implemented it will issue work orders for preventive maintenance, record all preventive maintenance activities, and maintain training records. The computer program is expected to be fully operational before the end of the 1999 calendar year.