PRO Cooperative Inc. - Bradgate - Executive Summary
PRO Cooperative Inc. - Bradgate |
Risk Management Plan - Executive Summary
The accidental release prevention policy at PRO Cooperative Inc. involves, but is not limited to technologies, procedures, and management practices. All applicable procedures of the ANSI K-61.1 - 1989 revision of the "Safe Requirements for the Storage and Handling of Anhydrous Ammonia," as adopted by the Iowa Department of Agriculture and Land Stewardship (IDALS) are adhered to. Our emergency response policy involves the preparation of response plans that are tailored to our facility and to the emergency response services available in our community, and is in compliance with the EPA Emergency Response Program requirements.
This facility is in the business of selling anhydrous ammonia to farm customers as a form of nitrogen fertilizer. The facility has two anhydrous ammonia storage tanks, one with a capacity of 11,800 gallons water capacity, and the other with a water capacity of 30,000 gallons. The storage
tanks, several anhydrous ammonia nurse tanks, risers for filling nurse tanks, electrical panels, lighting, and safety equipment are all parts of this facility's anhydrous ammonia operation. The facility is manned during the season and is operational through normal business hours.
The off-site consequences analysis includes two anhydrous ammonia release scenarios, identified as "worst-case" release and "alternative" release scenario. The first scenario is defined by EPA and shall assume the maximum quantity of one vessel is released as a gas in 10 minutes due to a catastrophic break. The alternative release scenario is defined as a more likely accidental release of anhydrous ammonia caused by a transfer hose failure.
The "worst-case" release scenario involves a catastrophic failure of the largest tank, releasing the entire 131,325 pounds of anhydrous ammonia. The off site consequences were calculated using "TFI's RMP Guidance for Ammonia Retailers". The worst case scenario used E
PA's recommended wind speed of 1.5 meters per second with a "F" atmospheric stability class. A rural topography was selected as typical. The distance to the endpoint was 2.6 miles. It is estimated that 359 people would be affected by this release.
The "alternative release" scenario assumed a hose breaks and leaks 7,127 pounds of anhydrous ammonia. The EPA recommended wind speed of 3.0 meters per second with a "D" atmospheric stability class was used in this scenario. Using urban topography and "TFI's RMP Guidance for Ammonia Retailers" the toxic endpoint is 0.46 mile. The population with in that area is estimated to be 316 people. The assumption is that the duration of the release is 2 minutes because equipment, excess flow valves, and human intervention will stop the leak.
PRO Cooperative Inc. has had no anhydrous ammonia leaks within the past five years. Even though the company has had no releases it still coordinates annual visits with the local fire department to review
the systems and procedures for response to a leak.
PRO Cooperative Inc. has several key elements in it's accident prevention plan:
1. The anhydrous ammonia system adheres to the laws and regulations that are based on the 1989 revision of the ANSI K61.1 adopted in 1990 by the State of Iowa.
2. Annual training is required of all personnel on handling, transferring, or transporting anhydrous ammonia. The training includes properties of ammonia, safe handling practices, first aid, and emergency response.
3. Use of good management practices as specified by industry standards and training aids.
4. Frequent site inspections by management and safety consultants.
5. Annual inspections by IDALS fertilizer inspectors include safety equipment, tanks, and handling equipment.
6. Use of proper anhydrous ammonia personal protective equipment and safety equipment.
Changes are made in the system when necessary or when required by regulation change. Periodic evaluations of the procedures help to det
ermine whether or not a change in operations should be made to provide increased safety to the operators and to the community.