Wal-Mart Distribution Center #6085 - Executive Summary
WAL-MART DISTRIBUTION CENTER #6085 |
RISK MANAGMENT PLAN
1. ACCIDENTAL RELEASE PREVENTION AND EMERGENCY RESPONSE POLICIES.
At this Wal-Mart Distribution Center (D. C.), we utilize anhydrous ammonia which is considered hazardous by the Environmental Protection Agency (EPA). The properties which make ammonia valuable as a refrigerant also necessitate certain safety precautions. Wal-Mart strives to protect all its valuable resources and assets - both personnel and property. We live and have families in this community. We want to prevent exposure to all our personnel as well as nearby members of our community, existing natural resources, and the surrounding environment. It is our policy to comply with all Federal, State, and Local regulations. Through continual, accurate training and various safety devices and procedures, we work to minimize potential releases.
Our emergency response program has specific procedures for accidental releases of an
hydrous ammonia as well as other emergencies. We work in conjunction with the Tomah Fire Department and the Local Emergency Planning Committee to prepare for necessary notification of all affected neighbors.
2. THE STATIONARY SOURCE AND REGULATED SUBSTANCES HANDLED.
The primary purpose of our facility is the temporary storage of refrigerated and frozen foods. We utilize anhydrous ammonia as the primary means for refrigeration and freezing. An outside company is used to fill our main receiver tanks. Piping then carries the ammonia to the needed refrigeration or freezing units. Access to the site is restricted to facility employees, authorized management personnel and authorized contractors.
The regulated substance used at our facility is anhydrous ammonia. The maximum amount of ammonia stored at this facility is 35,000 pounds. We have the capacity for more but our policy limits this amount not to exceed IIAR recommendations.
3. THE WORST CASE RELEASE SCENARIO(S) AND THE
ALTERNATIVE RELEASE SCENARIO(S), INCLUDING ADMINISTRATIVE CONTROLS AND MITIGATION MEASURES TO LIMIT THE DISTANCES FOR EACH REPORTED SCENARIO.
Worst Case Scenario
The worst case scenario would be failure of our largest receiver. Our policy restricts the maximum capacity of this 16,232 pound tank to 80% of capacity. The maximum quantity stored in this receiver is 13,025 pounds. It is assumed that the entire contents are released as a two phase flow (gas and aerosol-ALOHA).
Distance to endpoint: 1.0 miles
The alternative scenario would be the release of ammonia due to the failure of a pressure relief valve. The emergency alarms would signal monitoring personnel to notify a technician to take action. The maximum time of the release would be 60 minutes and maximum quantity released would be approximately 2,187 pounds of ammonia.
Distance to endpoint: 0.11 miles (or 192 yards)
4. FIVE-YEAR ACCIDENT HISTORY.
This is a newly constructed facility that opened
in February of 2000. At the time of this submission, the system had not been charged with ammonia. Consequently, this Wal-Mart D. C. facility has not incurred a reportable release.
5. THE RMP MANAGEMENT PROGRAM.
The management of the RMP program will be handled by the Maintenance Manager. He/She will administrate in conjunction with the Wal-Mart D. C. management and personnel. Other entities or organizations that will be coordinated with include the Monroe County Local Emergency Planning Committee and the Tomah Fire Department.
6. THE GENERAL ACCIDENTAL RELEASE PREVENTION PROGRAM AND THE SPECIFIC PREVENTION STEPS.
The Wal-Mart D. C. facility complies with all applicable Federal, State and Local regulations including the EPA's Accidental Release Prevention Rule. Our personnel are trained about this during our Hazard Communications Training and through access to our Written Programs. Our Refrigeration Maintenance operators receive classroom training and/or plus On-The-Job t
raining (OJT). They are given oral tests and are able to demonstrate proper job skills and knowledge. Also, the ammonia system is operated, tested and maintained to the standard of International Institute of Ammonia Refrigeration (IIAR), the most stringent standards of the industry.
7. THE EMERGENCY RESPONSE PROGRAM.
Wal-Mart D. C. has onsite Hazardous Materials trained personnel to immediately respond to adverse conditions. We have monthly meetings as well as annual certification. This helps minimize the potential of an off-site release.
We work very closely with the Local Emergency Planning Committee and the Tomah Fire Department on emergency preparedness. We meet periodically with representatives of each to address any changes in the facility or any new concerns.
8. PLANNED CHANGES TO IMPROVE SAFETY.
Currently, Wal-Mart D. C. trains and tests all refrigeration technicians. Our preventative maintenance program is above standard and our total ammonia Process Safety Pro
gram is reviewed annually and updated periodically. Our program is improved continuously through annual updates of our written program and annual training of our technicians. We also take advantage of new technologies when safer and more economical alternatives are available.
In December of 1999, Wal-Mart implemented the IIAR training protocol for their refrigeration technicians. The program consists of classroom training, viewing various training/safety videos and written testing procedures. The training will be conducted on at least an annual basis.